Terms of Success Part III – Humidity: Relative and Comparative Testing
This may not be an academic paper on the linguistics of concrete floor installation. Yet, we need only look to the definitions of two words to understand how their confusion leads to concrete moisture problems in flooring. Specifically, floor installation hinges on a contractor’s solid grasp of two methods of testing:
Relative: something dependent upon external conditions for its specific nature or size (opposite of absolute).
Comparative: using comparison as a method of study.
Everybody compares: two cans of soup at the supermarket, cars, stages of life, classes, flooring products, even friends. Look at one and assess; look at the other and assess; then, compare the two assessments. Translated to concrete slab, installers look at the result of one moisture test and compare it to the previous one. The trouble begins when the same contractor uses that assessment to conclude that a concrete’s moisture levels are dry enough for floor covering. Why? Simple (but deadly): comparison excludes all assessment of how concrete moisture is currently changing due to the conditions in the environment.
Environmental Influences on Concrete Moisture:
- location of water table
- presence (or not) of vapor barriers
- concrete mixture
- relative humidity and/or temperature of the air
- changes in ambient relative humidity and/or temperature
- moisture migration
- construction water spills
A comparative analysis relies on one overall reading to conclude that the above interactive factors are stable enough to install a floor covering.
All healthy concrete contains moisture. Even in prime condition, moisture exists. Installation challenges often result when job timelines do not permit adequate time for concrete to dry. Once concrete is poured, it forms and strengthens. It also pushes water vapors from the bottom of the slab to the surface, where they evaporate.
Relative Humidity Testing
The best way to assess concrete’s drying progression is to measure its relative humidity (RH) levels. That is, we need to measure the state of relative humidity (RH%) at various locations, at specific depths of a concrete slab. Put simply, a dry area is able to accept migrating moisture on its push to the surface. Wet areas need more time to dry. Relative assessment is based on the inter-connected states of relative humidity throughout a concrete slab. If it looks dry on the surface, how do we know that bottom moisture has concluded its migration to the surface? RH testing provides an accurate answer to that procedural question.
The relative humidity (RH%) test method is the best way to predict future flooring failures. Relativity humidity is the single most effective method that contractors can use to avoid concrete flooring moisture problems. It is based on multiple readings which are related. Together, they form a composite picture of the slab’s state of readiness. Wagner Meters has developed simple, convenient and cost-effective digital RH assessment. Installers use RH testing to safely make two crucial predictions. First, they can tell if the concrete itself is ready for floor covering. However, RH results also empower contractors to predict the bond strength of flooring adhesive products. In fact, successful builders must consider relative humidity when they choose compatible floor covering and adhesive products prior to installation.
When it comes to concrete, your ability to test correctly determines your installation success. Why compare when you can relate?
Video: “Relative Humidity (RH) Testing of Concrete Floors” by Howard Kanare.
Smith, Ron “Performing Correct and Accurate RH Testing in Concrete Slabs”; Wagner Meters; Web.
Kanare, Howard “Measuring Relative Humidity at 40%” (Graphic); Concrete Floors and Moisture.
2nd Edition. Skokie, Ill.: Portland Cement Association, 2008.
Terms of Success: Part I “Clarifying your Understanding – Resolve your Floor”
Terms of Success: Part II “The Real Dangers of Hydrostatic Pressure”
Latest posts by Jason Spangler (see all)
- How to Prepare a Concrete Floor for Coatings - September 14, 2016
- RH Testing and That 72-Hour Wait: How Do You Manage It? - August 9, 2016
- 5 Ways to Speed up Your Concrete Moisture Testing - August 5, 2016